## Description

size of contactor | S00 | |

product extension | ||

● function module for communication | No | |

● auxiliary switch | Yes | |

power loss [W] for rated value of the current | ||

● at AC in hot operating state | 1.5 W | |

● at AC in hot operating state per pole | 0.5 W | |

● without load current share typical | 5.7 W | |

insulation voltage | ||

● of main circuit with degree of pollution 3 rated value | 690 V | |

● of auxiliary circuit with degree of pollution 3 rated value | 690 V | |

surge voltage resistance | ||

● of main circuit rated value | 6 kV | |

● of auxiliary circuit rated value | 6 kV | |

maximum permissible voltage for protective separation between coil and main contacts according to EN 60947-1 | 400 V | |

protection class IP | ||

● on the front | IP20; IP20 | |

● of the terminal | IP20 | |

shock resistance at rectangular impulse | ||

● at AC | 7,3g / 5 ms, 4,7g / 10 ms | |

shock resistance with sine pulse | ||

● at AC | 11,4g / 5 ms, 7,3g / 10 ms | |

mechanical service life (operating cycles) | ||

● of contactor typical | 30 000 000 | |

● of the contactor with added electronically optimized auxiliary switch block typical | 5 000 000 | |

● of the contactor with added auxiliary switch block typical | 10 000 000 | |

reference code according to IEC 81346-2 | Q | |

Substance Prohibitance (Date) | 09/01/2022 | |

Ambient conditions | ||

installation altitude at height above sea level maximum | 2 000 m | |

ambient temperature | ||

● during operation | -5 … +60 °C | |

● during storage | -25 … +80 °C | |

relative humidity minimum | 10 % | |

relative humidity at 55 °C according to IEC 60068-2-30 maximum | 95 % | |

Main circuit | ||

number of poles for main current circuit | 3 | |

number of NO contacts for main contacts | 3 | |

operating voltage | ||

● at AC-3 rated value maximum | 690 V | |

● at AC-3e rated value maximum | 690 V | |

operational current | ||

● at AC-1 at 400 V at ambient temperature 40 °C rated value | 22 A | |

● at AC-1 up to 690 V | ||

— at ambient temperature 40 °C rated value | 22 A | |

— at ambient temperature 60 °C rated value | 20 A | |

● at AC-3 | ||

— at 400 V rated value | 12 A | |

— at 500 V rated value | 9.2 A | |

— at 690 V rated value | 7 A | |

● at AC-3e | ||

— at 400 V rated value | 12 A | |

— at 500 V rated value | 9.2 A | |

— at 690 V rated value | 6.7 A | |

● at AC-4 at 400 V rated value | 8.5 A | |

● at AC-5a up to 690 V rated value | 19.4 A | |

● at AC-5b up to 400 V rated value | 9.9 A | |

● at AC-6a | ||

— up to 230 V for current peak value n=20 rated value | 7.2 A | |

— up to 400 V for current peak value n=20 rated value | 7.2 A | |

— up to 500 V for current peak value n=20 rated value | 7.2 A | |

— up to 690 V for current peak value n=20 rated value | 6.7 A | |

● at AC-6a | ||

— up to 230 V for current peak value n=30 rated value | 4.8 A | |

— up to 400 V for current peak value n=30 rated value | 4.8 A | |

— up to 500 V for current peak value n=30 rated value | 4.8 A | |

— up to 690 V for current peak value n=30 rated value | 4.8 A | |

minimum cross-section in main circuit at maximum AC-1 rated value | 4 mm² | |

operational current for approx. 200000 operating cycles at AC-4 | ||

● at 400 V rated value | 4.1 A | |

● at 690 V rated value | 3.3 A | |

operational current | ||

● at 1 current path at DC-1 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 2.1 A | |

— at 220 V rated value | 0.8 A | |

— at 440 V rated value | 0.6 A | |

— at 600 V rated value | 0.6 A | |

● with 2 current paths in series at DC-1 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 12 A | |

— at 220 V rated value | 1.6 A | |

— at 440 V rated value | 0.8 A | |

— at 600 V rated value | 0.7 A | |

● with 3 current paths in series at DC-1 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 20 A | |

— at 220 V rated value | 20 A | |

— at 440 V rated value | 1.3 A | |

— at 600 V rated value | 1 A | |

● at 1 current path at DC-3 at DC-5 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 0.15 A | |

● with 2 current paths in series at DC-3 at DC-5 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 0.35 A | |

● with 3 current paths in series at DC-3 at DC-5 | ||

— at 24 V rated value | 20 A | |

— at 110 V rated value | 20 A | |

— at 220 V rated value | 1.5 A | |

— at 440 V rated value | 0.2 A | |

— at 600 V rated value | 0.2 A | |

operating power | ||

● at AC-1 | ||

— at 230 V rated value | 7.5 kW | |

— at 230 V at 60 °C rated value | 7.5 kW | |

— at 400 V rated value | 13 kW | |

— at 400 V at 60 °C rated value | 13 kW | |

— at 690 V rated value | 22 kW | |

— at 690 V at 60 °C rated value | 22 kW | |

● at AC-2 at 400 V rated value | 5.5 kW | |

● at AC-3 | ||

— at 230 V rated value | 3 kW | |

— at 400 V rated value | 5.5 kW | |

— at 500 V rated value | 5.5 kW | |

— at 690 V rated value | 5.5 kW | |

● at AC-3e | ||

— at 230 V rated value | 3 kW | |

— at 400 V rated value | 5.5 kW | |

— at 500 V rated value | 5.5 kW | |

— at 690 V rated value | 5.5 kW | |

● at AC-4 at 400 V rated value | 4 kW | |

operating power for approx. 200000 operating cycles at AC-4 | ||

● at 400 V rated value | 2 kW | |

● at 690 V rated value | 2.5 kW | |

operating apparent power at AC-6a | ||

● up to 230 V for current peak value n=20 rated value | 2.8 kVA | |

● up to 400 V for current peak value n=20 rated value | 4.9 kVA | |

● up to 500 V for current peak value n=20 rated value | 6.2 kVA | |

● up to 690 V for current peak value n=20 rated value | 8 kVA | |

operating apparent power at AC-6a | ||

● up to 230 V for current peak value n=30 rated value | 1.9 VA | |

● up to 400 V for current peak value n=30 rated value | 3.3 VA | |

● up to 500 V for current peak value n=30 rated value | 4.1 VA | |

● up to 690 V for current peak value n=30 rated value | 5.7 VA | |

short-time withstand current in cold operating state up to 40 °C | ||

● limited to 1 s switching at zero current maximum | 200 A; Use minimum cross-section acc. to AC-1 rated value | |

● limited to 5 s switching at zero current maximum | 123 A; Use minimum cross-section acc. to AC-1 rated value | |

● limited to 10 s switching at zero current maximum | 96 A; Use minimum cross-section acc. to AC-1 rated value | |

● limited to 30 s switching at zero current maximum | 74 A; Use minimum cross-section acc. to AC-1 rated value | |

● limited to 60 s switching at zero current maximum | 61 A; Use minimum cross-section acc. to AC-1 rated value | |

no-load switching frequency | ||

● at AC | 10 000 1/h | |

operating frequency | ||

● at AC-1 maximum | 1 000 1/h | |

● at AC-2 maximum | 750 1/h | |

● at AC-3 maximum | 750 1/h | |

● at AC-3e maximum | 750 1/h | |

● at AC-4 maximum | 250 1/h | |

Control circuit/ Control | ||

type of voltage of the control supply voltage | AC | |

control supply voltage at AC | ||

● at 50 Hz rated value | 230 V | |

● at 60 Hz rated value | 230 V | |

operating range factor control supply voltage rated value of magnet coil at AC | ||

● at 50 Hz | 0.8 … 1.1 | |

● at 60 Hz | 0.85 … 1.1 | |

apparent pick-up power of magnet coil at AC | ||

● at 50 Hz | 37 VA | |

● at 60 Hz | 33 VA | |

inductive power factor with closing power of the coil | ||

● at 50 Hz | 0.8 | |

● at 60 Hz | 0.75 | |

apparent holding power of magnet coil at AC | ||

● at 50 Hz | 5.7 VA | |

● at 60 Hz | 4.4 VA | |

inductive power factor with the holding power of the coil | ||

● at 50 Hz | 0.25 | |

● at 60 Hz | 25 | |

closing delay | ||

● at AC | 9 … 35 ms | |

opening delay | ||

● at AC | 4 … 15 ms | |

arcing time | 10 … 15 ms | |

control version of the switch operating mechanism | Standard A1 – A2 | |

Auxiliary circuit | ||

number of NC contacts for auxiliary contacts instantaneous contact | 1 | |

operational current at AC-12 maximum | 10 A | |

operational current at AC-15 | ||

● at 230 V rated value | 10 A | |

● at 400 V rated value | 3 A | |

● at 500 V rated value | 2 A | |

● at 690 V rated value | 1 A | |

operational current at DC-12 at 440 V rated value | 0.3 A | |

operational current at DC-12 | ||

● at 24 V rated value | 10 A | |

● at 48 V rated value | 6 A | |

● at 60 V rated value | 6 A | |

● at 110 V rated value | 3 A | |

● at 125 V rated value | 2 A | |

● at 220 V rated value | 1 A | |

● at 600 V rated value | 0.15 A | |

operational current at DC-13 | ||

● at 24 V rated value | 10 A | |

● at 48 V rated value | 2 A | |

● at 60 V rated value | 2 A | |

● at 110 V rated value | 1 A | |

● at 125 V rated value | 0.9 A | |

● at 220 V rated value | 0.3 A | |

● at 600 V rated value | 0.1 A | |

contact reliability of auxiliary contacts | 1 faulty switching per 100 million (17 V, 1 mA) | |

Short-circuit protection | ||

design of the fuse link | ||

● for short-circuit protection of the main circuit | ||

— with type of coordination 1 required | gG: 50A (690V,50kA) | |

— with type of assignment 2 required | gG: 20A (690V,50kA) | |

● for short-circuit protection of the auxiliary switch required | gG: 10 A (690 V, 1 kA) | |

Installation/ mounting/ dimensions | ||

mounting position | +/-180° rotation possible on vertical mounting surface; can be tilted forward and backward by +/- 22.5° on vertical mounting surface | |

fastening method | screw and snap-on mounting onto 35 mm standard mounting rail according to DIN EN 60715 | |

height | 58 mm | |

width | 45 mm | |

depth | 73 mm | |

required spacing | ||

● with side-by-side mounting | ||

— forwards | 10 mm | |

— upwards | 10 mm | |

— downwards | 10 mm | |

— at the side | 0 mm | |

● for grounded parts | ||

— forwards | 10 mm | |

— upwards | 10 mm | |

— at the side | 6 mm | |

— downwards | 10 mm | |

● for live parts | ||

— forwards | 10 mm | |

— upwards | 10 mm | |

— downwards | 10 mm | |

— at the side | 6 mm | |

Connections/ Terminals | ||

type of electrical connection | ||

● for main current circuit | screw-type terminals | |

● for auxiliary and control circuit | screw-type terminals | |

● at contactor for auxiliary contacts | Screw-type terminals | |

● of magnet coil | Screw-type terminals | |

type of connectable conductor cross-sections for main contacts | ||

● solid | 2x (0.5 … 1.5 mm²), 2x (0.75 … 2.5 mm²), 2x 4 mm² | |

● solid or stranded | 2x (0,5 … 1,5 mm²), 2x (0,75 … 2,5 mm²), 2x 4 mm² | |

● finely stranded with core end processing | 2x (0.5 … 1.5 mm²), 2x (0.75 … 2.5 mm²) | |

connectable conductor cross-section for main contacts | ||

● solid | 0.5 … 4 mm² | |

● solid or stranded | 0.5 … 4 mm² | |

● stranded | 0.5 … 4 mm² | |

● finely stranded with core end processing | 0.5 … 2.5 mm² | |

connectable conductor cross-section for auxiliary contacts | ||

● solid or stranded | 0.5 … 4 mm² | |

● finely stranded with core end processing | 0.5 … 2.5 mm² | |

type of connectable conductor cross-sections | ||

● for auxiliary contacts | ||

— solid or stranded | 2x (0.5 … 1.5 mm²), 2x (0.75 … 2.5 mm²), 2x 4 mm² | |

— finely stranded with core end processing | 2x (0.5 … 1.5 mm²), 2x (0.75 … 2.5 mm²) | |

● for AWG cables for auxiliary contacts | 2x (20 … 16), 2x (18 … 14), 2x 12 | |

AWG number as coded connectable conductor cross section | ||

● for main contacts | 20 … 12 | |

● for auxiliary contacts | 20 … 12 | |

Safety related data | ||

proportion of dangerous failures | ||

● with low demand rate according to SN 31920 | 40 % | |

● with high demand rate according to SN 31920 | 73 % | |

B10 value with high demand rate according to SN 31920 | 750 000 | |

failure rate [FIT] with low demand rate according to SN 31920 | 100 FIT | |

IEC 61508 | ||

T1 value for proof test interval or service life according to IEC 61508 | 10 a | |

Electrical Safety | ||

protection class IP on the front according to IEC 60529 | IP20 | |

touch protection on the front according to IEC 60529 | finger-safe, for vertical contact from the front |